MIT Solenoid Dosing Pumps, acid, chlorine, liquid manure etc. Designed to be used in place that should be given in doses of chemicals are precision dosing device. (pool, drinking water, agricultural irrigation )
Areas of usage: Swimming Pools, chemical fluid transfer, Car Wash Fluids, Cooling Towers, Reverse Osmosis (RO) Systems, Original Equipment Manufacturers, Capacity values were obtained as a result of tests made under standard conditions with water.
Mono pumps are used in various industries, in most tough applications, without any problem, it can transfer fluids.
As it is suitable for transferring high and low viscosity fluids it can also transfer abrasive, sticky, crush and foam sensitive fluids. It provides a measurable, smooth, linear flow with quiet and vibration-free operation.
MIT Apartment and Local Heating Network Transfer Stations, combines the economy provided by central heating systems with the advantage of determining independently comfort conditions offered by individual systems.
Thus, this system which significantly reduces energy consuptions, helps also to provide an individual sharing in central system fuel consumptions.
Ekin Industrial has entered the heating - cooling sector by selling plate heat exchanger first. Since that time, Ekin has expanded into new and upcoming investments with its customer focused vision and dynamic approach.
One of the main steps was gaining the identity of being a producer. Ekin Industrial has started the production of plate heat exchangers with the brand of 'MIT'
We grew in the philosophy of quality, through initially adapting to ISO Quality Management System procedures, and completed the CE security and quality certification period, and have matched foreign standards like GOST.
Heat exchangers are used to exchange heat between two fluids. Plate heat exchangers are high performance components and provide a high level of efficiency combined with compact dimensions and low weight.
Water glycol (coolants)
HFC operating fluids
The quantity of particles in suspension should be less than 10 mg/l.
Particle size < 0.6 mm. (spherical).
Thread-like particles cause a rapid rise in pressure drops.
50°C to 437°F (10° to 225°C)(freezing point and boiling point must be taken into consideration!)
max. 49 psi (3 bar) (static) up to 257°F (125°C)
max. 435 psi (30 bar) (static) up to 437°F (225°C)
test pressure: 650 psi
The following limits refer to a pH value of 7
free chlorine, CL2 < 0.5 ppm
chloride ions CL < 700 ppm at 20°C, < 200 ppm at 50°C
ph 7 - 10
Sulphate SO4 2-< 100 ppm
[H CO3 -] / [SO4 2-] > 1
ammonia, NH3 < 10 ppm
free CO < 10 ppm
The following ions are not corrosive under normal conditions:
phophate, nitrate, nitrite, iron, manganese, sodium and potassium